High-resolution data is useful for troubleshooting equipment. To collect high-resolution data, you can use burst mode.
Burst mode has to be configured.
Complete the following steps to force trigger and view a periodic acquisition.
Double-click the device from which you want to collect high-resolution data.
Device Properties tab, select the
Enable Burst Mode checkbox and configure the
Burst Collection Settings. If you make changes in this step, update the device configuration on the
Devices tab of the Device Configuration page.
on the Trend viewer toolbar and select
Collect Burst Data Sets.
Ensure the workspace is configured to load data from the appropriate time range.
If the Trend viewer already contains curves for the features or sensors of interest, click
Refresh trend data
in the viewer toolbar. You may need to wait a few minutes to see high-resolution data in viewers, because devices must switch
to burst mode, perform the high-resolution data acquisition, and send the data to the NI InsightCM server.