Last Modified: September 6, 2017
You can set the flash period for any output.
Figure 1. Flash Period
The flash period is defined by the time the output is on plus the time the output is off. The output on/off time equals half of the flash period.
Set the signal value to DOn = flash in the state machine diagram to use the flash period.
Set the flash period large enough to allow the readback diagnostic to run: Flash period > 2 × Readback response time
When using test pulses, set the flash period large enough to allow the test pulse to run: Flash period > 2 × Test pulse period
Recently Viewed Topics